BS8418:2015 UPS System Selector
Many moons ago we blogged about BS8418:2010 (Installation and remote monitoring of detector-activated CCTV systems, Code of Practice) and the requirements for UPS Systems. That standard stated:
Unless the mains power supply is supplemented with a stand-by generator, an uninterruptible power supply (UPS) must be able to power the CCTV control equipment and communications devices for a minimum of 4 hours after mains power failure. Where the mains power is supplemented by a stand-by generator, the UPS needs to be capable of providing stand-by power for a minimum of 30 minutes after mains power failure (for example if the stand-by generator does not start).
The 2015 revision relaxed this somewhat, allowing for a documented threat assessment and risk analysis to determine whether a UPS is required or not. That said, it is difficult to state how any threats or risks are mitigated against a loss of power without a UPS, so the requirement for UPS Systems is likely still to remain in BS8418:2015 installations.
If a UPS is used as the “alternative power source” then this has been changed from a 4 hour requirement to a 30minute requirement when supporting control equipment and data transmission devices. However the standby power capability for the detectors and semi-wired detectors remains at 4hours.
Find a UPS Solution
Enter in your load power and how long you need the UPS to provide backup power for. The UPS Selector will identify any UPS that meet your requirements.
You can filter the selection based upon required features, by clicking the checkbox. Many models are available to by online from our webstore but contact us using the form below for specific requirements or for other products not available to purchase online.
This cannot be blank.
Contact Us About This Solution
Available Tags#powercut ag1500s ag series announcements B16 Cabs Battery Battery Backup Battery Recharge buck and boost Bypass Switch case studies christmas customers dc ups door access fan noise inverter iPower isolation transformer line interactive line interactive ups lithium Long Runtime Modem motor selection power inspired power quality pricing regen regenerator Router Runtime shutter door solar transfer time tx series uninterruptible power supply ups UPS Calculator ups runtime calculator UPS Selector UPS Systems vis2000b voltage white paper